Common Glow-worm Boiler Problems & Repair Advice
This guide to the most common Glow-worm boiler problems will help you through the hard times and could even see you fixing a fault yourself. Should you be in any doubt at all or identify a fault that needs an engineer, you can get a free boiler repair quote with our service.
Need a boiler repair?
|Glow-worm Boiler Problems||Glow-worm Error / Fault Code|
|Low water pressure||108 or F22|
|Flame detection fault||F16|
|No heating or hot water||501|
|Frozen condensate pipe||F1, F4, F28 or F29|
|Printed circuit board (PCB) fault||F13|
If the pressure gauge on your Glow-worm boiler is showing anything below 1 bar then you may have an issue which can lead to your central heating system not functioning as well as it should. Over time, boilers will gradually lose pressure but a sudden drop could mean there’s a fault somewhere in the system, commonly a leak.
Increasing low boiler pressure
If you spot a leak around the heating system, turn off the water supply and contact a Gas Safe registered engineer, likewise if there’s been a sudden drop in pressure. For any gradual decreases in boiler pressure, it’s possible to repressurise the system yourself by following the steps in our guide to low boiler pressure. If you don’t feel safe doing this or aren’t overly sure about what today, contact a heating engineer to do it for you.
Once the pressure is back up to around 1.5 bar, your Glow-worm boiler should have sufficient pressure to work again. Increase the pressure too much (above 2 bar) and you’ll then have a problem with high boiler pressure, which could damage the unit.
If F16 displays on your boiler, there’s a flame detection fault with your boiler.
Turning the hot water tap calls the printed circuit board (PCB) into action, telling the burner to fire up so that the water can be heated, which involves the gas valve supplying sufficient fuel. When the F16 error code appears, there’s an issue preventing this process form happening – either the flame isn’t present or the PCB is failing to detect the flame.
How to fix the F16 error code
Never attempt to fix the F16 error code on a Glow-worm boiler yourself, always hire a Gas Safe registered engineer. There are many potential issues that they will look into, diagnose and be able to repair:
- Flame sensor damage
- Faulty PCB
- Blockage in the burner jet
- Gas valve issues
- Blocked flue or condensate pipe
There are many potential reasons why there’s no heating or hot water in your home, including broken diaphragms and airlocks, failure of motorised valves, issues with the thermostat or low water levels.
How to get the heating and hot water back on
Start out by checking if the boiler pressure is too low (below 1bar) and that the temperature is set high enough for the heating to come on. In addition to these, if you’re on a prepayment meter then it’s worth making sure that you have enough credit.
Should you go through these and not see any problems, it’s time to contact a Gas Safe registered engineer as there’s likely to be an issue within the unit.
A condensate pipe on condensing boilers transports the acidic water, caused by waste gas, away from the boiler. This usually runs outside into a drain so in the colder months being outside can lead to it freezing over.
Thawing a frozen condensate pipe
Thawing out a frozen condensate pipe is something you can do yourself without the need for a fully-qualified heating engineer, in fact, you can find out how to do it using our guide to thawing a frozen condensate pipe. While this is something you can do yourself, don’t feel like you have to do it, if you feel the slightest bit unsure or unsafe, don’t hesitate to contact a Gas Safe registered engineer.
Any strange noises you’re hearing could be caused by a variety of things including air in the system, alternatively the water pressure could be too low or it’s kettling. You might be able to determine the type of problem your boiler is having based on the type of noise it is making. Take a look at our guide to central heating noises to help you determine the cause of your noisy boiler.
The printed circuit board (PCB) is effectively the ‘brain’ of modern boilers as it sends and receives signals from all the electrical components within the unit. A faulty, broken or unconfigured PCB will prevent your Glow-worm boiler from working properly.
How to fix a faulty PCB
An issue with the PCB is commonly seen after a new one has been fitted due to the incorrect model being installed or it being unconfigured. In the case that one of these is the problem, a heating engineer will be able to safely replace or configure the PCB.
However, if the PCB is broken then a new one will have to be fitted, which can come at a fairly large expense, so you might want to consider a new boiler. Especially because an issue with the PCB can bring to light issue with other electrical components, such as the pump and fan.
Need a boiler repair?
Identify the possible cause of a fault with your boiler using the table below, it will also let you know if you’ll need an engineer.
|Problem||Possible Cause||Do you need an engineer?|
|No heat or hot water||Broken diaphragms and airlocks, failure of motorised valves, issues with the thermostat or low water levels||Yes|
|Leaking and dripping||Most common cause is a broken internal component but it will depend where the water is leaking from||Yes|
|Banging, whistling or gurgling noises||A common cause is air in the system, alternatively it could be that the water pressure is too low or it’s kettling||Yes|
|Pilot light goes out||Could be a broken thermocouple which is stopping the gas supply||Yes|
|Losing pressure||There could be a water leak in the system, the pressure relief valve needs replacing or the radiators have been bled recently||No unless there’s a leak|
|Frozen condensate pipe||Your boiler should display a fault code or warning notification||Yes|
|Thermostat issues||Thermostat may be turned off or not set to the correct settings (time etc.)||Consider replacing|
|Kettling||Limescale or sludge building up on the boiler’s heat exchanger||Yes|
|Radiators not getting hot||Sludge or air build up in the system or an unequal distribution of heat||You will need to bleed the radiators which doesn’t require an engineer unless you don’t feel like carrying out the task yourself.|
|Boiler keeps switching itself off||Could be low water pressure, a problem with the thermostat or a lack of water flow due to a closed valve, air in the system or the pump not circulating the water in the system correctly||Yes|
Faults with your Glow-worm boilers will be displayed as error codes to help you identify the issue. Familiarise yourself with the error codes using our list of Glow-worm error codes.
When you’ve had your Glow-worm boiler for a long period of time, you might be thinking about getting a new one installed. A brand new boiler could be saving you up to £305* a year if you live in a detached home. The table below shows how much you could be saving depending on your current boiler rating and property.
|House Type||G (<70%)||F (70-74%)||E (74-78%)||D (78-82%)|
|Mid terrace house||£175||£120||£105||£105|
|Mid terrace house||£95||£65||£55||£55|
If you’re looking to replace your Glow-worm boiler then a Gas Safe registered engineer will be needed to carry out the installation. The decision you have to make is whether to go with a local engineer or national company.
With local engineers, you’re likely to be offered a very competitive rate and they’re likely to deliver a personal service throughout your communications.
National companies may cost slightly more but you’ll have the safety of big brand protection and they could provide extra services such as ongoing boiler cover.
We recommend getting up to 3 quotes from different engineers when considering who should carry out any boiler-related work. Using our service you can get free quotes from reliable engineers near you.
If your boiler warranty has ended or will be coming to an end soon, it might be worth considering boiler insurance. This insurance can be taken out with your energy supplier, but there’s absolutely no obligation to do so. When comparing boiler insurance, keep an eye out for ones that offer annual service and safety inspections.
Glow-worm boilers come with 2-7 years of warranty as standard but some models are eligible for up to 15 years of warranty through Glow-worm’s club energy installers. Find out more with our guide to Glow-worm warranties. Keeping the warranty valid means arranging for an annual service of your Glow-worm boiler that will also ensure the safe and efficient running of the unit.
Find trusted engineers near you with our free service by sending us an enquiry today.
*According to the latest figures from the Energy Saving Trust
Get Glow-worm Boiler Quotes
Get quotes to supply and fit a new Glow-worm boiler now